In WorkPlace Tech can a SNVT exist in a Custom Object?
I/A Series WorkPlace Tech 4.0 and higher.
Custom Object Rules
Nearly all types of WP Tech shapes may be included on the Definition page of a Custom object, There are several exception and "SNVT objects" is one of them. This object must be on the top page of any control logic drawing instead.
For additional exceptions see WorkPlace Tech Tool 4.0 Engineering Guide (F-27254-3), Chapter 3 "Custom Object Rules"
When using DCT version 11.6, modifying the MSC-NCM schedule start-stop times do not save. The time reverts to the setting before the change was attempted.
Version 11.6 of DCT has an error in the compiled code.
Instead of starting DCT from the desktop shortcut, launch it from the DCT folder (double-click DCTGL.EXE).
Modify occupied cooling and heating (nciSetPts) variables on Viconics VT7652 LON stat, but changes are not transmitting to thermostat.
Have a DynamicCmd object linked up and can write the values in the DynamicCmd but they don’t ever change in the thermostat and they don’t show up in the nvoEffectSetPt variable.
VT7200 LonWork series
VT7300 LonWork series
VT7600 LonWork series
Setup of limits
Check the HeatMaxSetpoint and CoolMinSetpoint limits found in the nciCfgRtuHP ( Vt76Pir properties).
When a change that is outside of the limits, it will take the request but will not transmit change down to the thermostat.
In WorkPlace Tech Tool, the Definition tab of a Custom Object, right click on any object to request Properties info. The response is an error "Exception happened finding Visio shape".
What does this mean?
WorkPlace Tech Tool 5.7.x
There was an error in Visio.
The custom object may have been copied from a newer version of Visio to an older version.
There may have been an error when creating the custom object.
Shapes may have been added to the custom object when opened directly in Visio instead of being opened in WPTech.
Some other corruption to the drawing took place.
Do a “Rebuild Application”, and then try opening the shape properties again. If this does not work, try creating a new custom object, and then try copying the contents of the old custom object definition page into the new custom object definition page (while in WPTech). Then delete the old custom object, and then try the shape properties in the newly created custom object.
Unable to connect with DCT to log in MicroSmart MSC-NC
Flash Memory got corrupted.
Reloading Flash Memory on an MSC-NC (M)
Power down; jump J1 (near processor); power up.
Can DCT connect?
If so, remove J1 jumper
Do Alt-L to start Load Flash ROM installation
If unable to connect with DCT, will need to consider replacing/repairing unit.
Need to replace Analogue Timeswitch for Satchwell SVT4201, CSC 1776, CSC 1777, CSC2776 or CSC2777 Controller.
Faulty Timeswitch requires replacement.
Replacement Analogue Timeswitch for Satchwell SVT4201, CSC1776, CSC 1777, CSC2776 or CSC2777 Controller is part number 561-9-260.
The word TEST is displayed on the Liquid Crystal Display screen of a Satchwell Climatronic Controller when first powered up during initial installation preventing it from being commissioned.
The cause of the word TEST being displayed on the Liquid Crystal Display screen of a Satchwell Climatronic Controller when first powered up during initial installation and preventing it from being commissioned is normally due to a micro processor programming error occurring during the course of production.
There is no field remedy that can be applied to a Climatronic Controller displaying the word TEST on the Liquid Crystal Display screen that will enable it to be commissioned successfully.
The Controller should therefore be returned to the vendor for replacement under the terms and conditions of the warranty applicable at the time of purchase.