How to troubleshoot and solve issues configuring the EcoStruxure IT Gateway
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
Support for unsafe ciphers was removed as part of a security update in EcoStruxure IT Gateway version 1.8.0. NetBotz 4.x devices must now support 2048 bit certificates.
Devices that do not meet this requirement do not discover in Gateway 1.8.0 and newer. There is no indication of a certificate error when you run a new discovery.
When you update your Gateway from a previous version, NetBotz devices are listed as offline.
Install a new 2048 bit certificate on the NetBotz device. Self-signed automatically generated SSL certificates use 2048-bit encryption as of NetBotz version 4.5.4.
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login