It's your place to connect with experts and peers, get continuous support, and share knowledge.
Contact SchneiderCommunity.Support@se.com if you have any questions.
I had believe that at least one PowerLogic had the ability to be used in direct current applications? This would be at datacenter sites to read the battery bus voltage. Maybe the ION 7650? Did some research and could not find anything conclusive.If a…View more
TEAM:Once upon a time when I worked for Schneider-Electric we had a tool called Loop 2k that let us scan for devices on networks. This was a real time saver and gave us proof of life for devices in a system. It let us pick what type or devices we bel…View more
TEAM:Since Schneider is relying so much on BACnet I would love to see and attend a detailed class on advanced networking subjects for this protocol. It can get very deep, cold and oxygen deprived while trying to use BANnet over subnets. Even RS485 ca…View more
TEAM:Is there a gateway from Schneider that allows data from EM4300 meters to be read by PME or is this strictly a building product? Since it does Zigbee it can be integrated with an MPM that translates to BACnet for an Automation Server or Enterpris…View more
Have reviewed the User Manual 7EN02-0356-02 06/2016. It is likely that we will have customers with application for this device. Confused by three things?1. Int242. Int483. Clusters and AttributesWe are very familiar with Modbus registers and BACnet o…View more
TEAM:Here is a screen capture of what we are reading for one of the iem3555 meters at a site.Note that current A is a significantly higher than B or C ampere readings and the kW is negative.Does anyone have a guess on why this would be? All that I ca…View more
ION Setup has an entry for this meter but appears to be lacking live data table for this type. This is .16xxxx that we had believed to be the newest. Found .17xxxx and at least we do not get the "no tables found" error. Won't know if this is the fix …View more
TEAM:We have one EM4200 and twelve iem3000 On a Daisy-Chain with a Link 150. The serial port was set to 9600, None, Stop Bit Automatic. The iem3000 units came in fine but the EM4200 (new Enercept) would not communicate.The fix is to change the stop b…View more
|Date Last Visited||
2019-08-16 02:06 AM