It's your place to connect with experts and peers, get continuous support, and share knowledge.
Contact SchneiderCommunity.Support@se.com if you have any questions.
This was originally posted on APC forums on 6/15/2009Does anyone know how to silence the email notification for a bad battery on the network management interface, or on the unit itself? I can't stop the notifications...
This was originally posted on APC forums on 2/15/2010We have VoIP phones that loose connection after we simulate a transfer to our generator. Nothing else looses power of course...but for the however many milliseconds that it takes to transfer to the…View more
This was originally posted on APC forums on 10/30/2009We have 2 PDU's that are 24A 200-240v. My question is, does this need to be plugged into a "2 pole" circuit? I have a receptacle with is L6-30, and the breakers are 1 pole 120/240. Would this work…View more
This was originally posted on APC forums on 5/19/2009How do you tell if a circuit is 2-pole or 3-pole? Is that the number of slots it takes up on the circuit panel? Apparently an L6-30 is a 2-pole, 3 wire configuration of 30A 125-250V, and L10-30 is …View more
This was originally posted on APC forums on 5/18/2009Hello, We have two L6-30 receptacles available that are evenly balanced on phases…except that the 2 circuits we have available to use are going to the APC that has a bad power module. It believe it…View more
This was originally posted on APC forums on 11/6/2009Hello, We powered up a new hp blade enclosure today, to what I supposedly thought was phases 1 & 3 of our Symmetra unit. Before powering up the enclosure, the phases were as followed: Output Watts …View more
This was originally posted on APC forums on 7/20/2009We had a bad power module in our Symmetra 40k. The power module has been replaced, and I cleared out the fault, but the fault keeps coming back. Now I have the alarm set for "Alarm If Redundancy Un…View more
|Date Last Visited||
2021-06-24 06:53 PM