It's your place to connect with experts and peers, get continuous support, and share knowledge.
Contact SchneiderCommunity.Support@se.com if you have any questions.
Looking for the accuracy of the following demand measurements in the PM8000: - Current demand - Active power demand - Reactive power demand - Apparent power demand Thank you!
Find more articles tagged with: english
I have an application where we need to record Freq. and kW at 32 samples per second (not cycles). A Setpoint module will trigger the recording if the Frequency goes out of bounds. However, I cannot figure out if we can have a Data Recorder module log…View more
Find more articles tagged with: ion8650
Given the high sampling rate of the ION9000T, what Potential Transformers (PT's) do you recommend for monitoring a 15kV system? The concern is that a regular transformer may "mask" or filter the high-speed transients going through it such that the me…View more
Find more articles tagged with: ION9000T
Is it possible to somehow calculate Standard Deviation in an ION meter (ideally PM8000)? We have an opportunity to sell multiple PM8000's to a firm that audits wind turbine production. We can meet everything they need to do except calculating Standar…View more
In case of PM5563 and also PM8000 does the demand shown on the meter display switch between kW, MW, GW ? If so, what is the boundary at which this switching happens?Does this affect the numbers that are read through communications? Is it possible to …View more
The CM2xxx meter can capture 64 and 128 point/cycle waveforms. In SMS and PMCU software, the user can manually trigger both the high-resolution and the low-resolution waveforms. However, when using PME or ION Setup to initiate a Manual Waveform Trigg…View more
Is it possible to factory reset an ION6200 meter in the field? I know about the "Reset Mode" that resets energy, demand, etc. but I need to reset all parameters back to default. I know some of the ION meters had a "special password" that would reset …View more
I have an application where a number of ModBus devices (Enercept meters) are connected serially to an EGX100. Is it possible to use the PM8000 to do data logging for these devices over the TCP/IP network?The alternative is to use an EGX300 (or Com'X5…View more
Can the dual Ethernet ports in the back of the PM5000 or PM8000 be used as an Ethernet switch to transport other protocols? For example let's say there is a PM8000 and downstream from it is a BACnet device. Can we use one of the ports on the PM8000 t…View more
A customer has some relatively old ION7500, ION7600, ION7550, ION7650 meters. I think the oldest one is an ION7500 with firmware rev 7500V207. They want to add Ethernet com cards to these meters.Is there a minimum firmware requirement for adding an E…View more
|Date Last Visited||
2 weeks ago