Metering & Power Quality
Schneider Electric support forum about Power Meters (ION, PowerTag, PowerLogic) and Power Quality from design, implementation to troubleshooting and more.
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
In the registers table of the PM8000 we have the register 54395 dedicated to display if the configuration of the frequency is 50Hz or 60Hz.
If I read the this register in INT16 I got -1 (1111 1111 1111 1111 in binary).
It is normally 1 or 0 in INT16 why it is -1?
It is written that this register is in R/W and I tried to write 0 (50Hz) and I got a modbus exception answer code 512.
Should I need to use a protected command in the same way as PM5000 but it is not mentioned in the table of registers of the PM8000_Modbus_Map (excel file)
In the web page the configuration of 50Hz Vs 60Hz is working fine but the customer want to perform that through a com Modbus configuration.
Thanks for your help.
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login