Important Announcement: Community Back to Full Functionality
Dear Members, we are thrilled to announce that our Community is back to full functionality and that posts publication is now enabled again! We appreciate your patience during the last weeks. Learn more about our Community Guidelines. Thank you, Schneider Electric Community Team.
PM5560 > PAS800
Metering & Power Quality
Schneider Electric support forum about Power Meters (ION, PowerTag, PowerLogic) and Power Quality from design, implementation to troubleshooting and more.
Panel Server Advanced and Universal are supporting max 64 downstream TCP connections (ETH devices). You can also connect up to 32 Serial devices without repeater. But just like Com'X, you may face some performance issues if you connect to much devices. For the moment, we have no documentation giving a "weight" per device and mentioning what is the maximum "weight" for the Panel Server.
Now my questions:
How do do you want to connect the PM5560 ? Through Serial or Ethernet ?
How many topics do you want to log ?
What will be your publishing frequency ?
Publishing on SFTP or Cloud Services ?
In any case, the Panel Server may not be suitable for all 78 PM5560. You may need to divide your architecture with 2x PAS800 with 39x PM5000 connected to each.
Romain POLETTE Solution Architect - France Operations