Important Announcement: Community Back to Full Functionality
Dear Members, we are thrilled to announce that our Community is back to full functionality and that posts publication is now enabled again! We appreciate your patience during the last weeks. Learn more about our Community Guidelines. Thank you, Schneider Electric Community Team.
ION 7400 and PM8000 Phasor Diagrams not correct
Metering & Power Quality
Schneider Electric support forum about Power Meters (ION, PowerTag, PowerLogic) and Power Quality from design, implementation to troubleshooting and more.
Link copied. Please paste this link to share this article on your social media post.
Your PM8000 is in DEMO mode. The Phasor viewer visible from the front panel is a fixed value with slight randomization applied to it (i.e. V2 angle with be approx. 120 degrees +/- 1) while ION Setup is reading the actual value being computed by the Harmonics Measurement modules (same applies for all harmonics displays on the front panel while the device is in DEMO mode).