Our customer is configuring IEC61850 function for PM8000.
They want to use RCB function for the protocol between system(client) and the meter.
Could you anyone who has an experience for that let me know how to the way - which tool and how, procedure?
Thank you for your help in advance.
I would recommend contacting technical support with your question.
Having said that, the following documents highlights the IEC 61850 and ION Technology that is supported by the PM8000: IEC 61850 and ION technology - EN - Download Schneider Electric
If you want to make any configuration changes to the current RCB's that are supported by your ICD file for your PM8000 device, you will need an IEC 61850 configuration tool, such as CET850, to change it and create a new CID file to upload to the meter's FTP directory.
Hi Jeong-Je Park,
BFO case 31620613 is created for your question, I need more information from you.
I will help you to provide solution in BFO.
I'm sorry that I've not got what you need yet.
But I have an update from our customer.
They succeeded in connecting two clients to PM8000.
For now they have only two questions.
Regarding getting data refresh issue,
They say that their own device that is not from Schneider Electric has
three value - Time, Value, Quality in MMXU1 PhV
But PM8000 has only value, not Time & Quality. So they think that's why
they can't get the information saying "Good Quality" from PM8000.
Can we make the information for Time & Quality for PM8000 available?
PM8000 supports NTP?
If so, how can we add the information for IP address of NTP Server?
Thank you for your support!!
Hello Jeong-Je Park,
I have sent my comments and extra information requests to L2 support Rohit Daftari.
Case number: 31620613 and 31760323.
Please contact directly with Rohit Daftari. We will help you to solve your issue in BFO.