LonWorks Device is Offline in Vista, but Online in LonMaker.
For Xenta Programmable devices refer to Xenta Programmable Device is Offline in Vista but Online in LonMaker.
- LonMaker, NL220
- Vista Workstation
- LonWorks Device
If the Vista database has some LonWorks devices that are not communicating, one cause could be due to changes in the system such as moving controllers to a new channel for example. Updating the Vista database with the system plug-in might not fully overwrite all the node properties causing the device not to communicate in Vista Workstation even though it is communicating in the LNS database.
- Delete the LonWorks device from the TAC Network in the System plug-in.
- "Update Vista Database" in the System plug-in to remove the device or devices from Vista Workstation.
- "Update TAC Network" to add the devices back to the TAC Network.
- "Update Vista Database" again to add the devices back to the Vista database.