APC UPS Data Center & Enterprise Solutions Forum
Schneider, APC support forum to share knowledge about installation and configuration for Data Center and Business Power UPSs, Accessories, Software, Services.
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
This was originally posted on APC forums on 12/7/2015
We have to ship the SUA3000XL with external batteries in a rack we build.
1. Is it required to disconnect the batteries as per the manual?
2. Can we put it in brain-dead mode to disconnect the batteries from the circuitry in lieu of physically disconnecting the batteries?
3. If batteries need to be disconnected, for the external batteries can we just disconnect the connection to the UPS?
4. Can you tell me the DOT and IATA regulations which govern the battery shipments?
This was originally posted on APC forums on 12/8/2015
Please disregard this post. We plan to disconnect the front batteries to break the circuit.
See Answer In Context
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login