Link copied. Please paste this link to share this article on your social media post.
Posted: 2021-07-0903:12 AM
This reply was originally posted by Bill on APC forums on 5/2/2016
"A-" in the stat section refers to the application file - the firmware file that tells the NMC what type of unit it is installed in - has failed to load for some reason. If the application does not load, you would still be able to connect to the NMC via telnet/FTP, and still be able to pull up a webpage from the IP address, but no information would be present. If this occurs, rebooting the card will cause the application to attempt to reload. If the issue is still not resolved, it may be necessary to reflash the firmware of the device.
See Knowledge Base document FA156047 for assistance with flashing the firmware.