APC UPS Data Center & Enterprise Solutions Forum
Schneider, APC support forum to share knowledge about installation and configuration for Data Center and Business Power UPSs, Accessories, Software, Services.
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
This question was originally posted by Oladayo on APC forums on 1/26/2017
What does the raw data below translates into:
M States = 00 02 02
The UPS failed to turn on load both in normal mode & bypass mode.
Looking forward to a prompt response.
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login