EcoStruxure IT forum
Schneider Electric support forum about installation and configuration for DCIM including EcoStruxure IT Expert, IT Advisor, Data Center Expert, and NetBotz
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
This question was originally posted on DCIM Support by josep.vilar on 2018-01-29
We have DCE 7.5 managing 5 Symmetra 160K. When we try to run kWh report, we can't select any sensor so we can't run kWh. Other reports run properly.
How we can do to get kWh reports?
Thanks in advance.
This answer was originally posted on DCIM Support by Balaraman Jagadeesan on 2018-01-29
Are you able to view Kwh value as the device sensor value in DCE software for Symmetra PX 160 K under view device sensors value?
In order for the DCE to generate the report of the sensor values, the sensor value should be present in the device for which you are generating the report.
As far as I remember, Symmetra 160 K UPS does not have Energy Kwh value reported via SNMP. If this sensor value is not present, then DCE will not be able to generate the report on Kwh.
I hope it answers your query.
. Last Modified:
This question is closed for comments. You're welcome to start a new topic if you have further comments on this issue.
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login