Link copied. Please paste this link to share this article on your social media post.
Posted: 2022-02-1107:46 AM
High Battery Temperature and Output Relay Critical (in Closed) Alarms
We have a Symmetra LX 16000 which has alarmed with a Battery 2: High Temperature alarm. Within a second it also generated a fault on the integrated Environmental Monitor Output Relay (Int Relay at Int Relay Location). According to the Management interface the output relay is in a closed state, but it's normal state is open. It will be a few days before we receive the replacement battery. My question is: Should we be taking any protective measures, such as putting the UPS in manual bypass and removing Battery 2 in the interim?
I've attached relevant screenshots and the recent event log in the PDF.
I am an end user with limited UPS knowledge, so please respond in layman's term as much as possible.