APC UPS Data Center & Enterprise Solutions Forum
Schneider, APC support forum to share knowledge about installation and configuration for Data Center and Business Power UPSs, Accessories, Software, Services.
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
This question was originally posted by Edwin on APC forums on 10/17/2016
I got an issue on one of my ATS. Yesterday, our building was testing their power, and suddenly few servers had been rebooted.
Those servers are connected to the ATS, and there are two power source are connected to it.
One is from the building, and another one is from my UPS.
I checked inside the UPS, it's running low usage, and the battery is fine, all servers which connected to the UPS have no issue.
The problem is on the ATS. Then, I logged into the ATS and check, I found the following:
Source A which is from the building, and it failed to fail over to source B
The ATS didn't reboot as well, the up time is over 180 days,
Anyone saw this issue before?
This reply was originally posted by Shanon on APC forums on 10/18/2016
I am sorry that you are having issues with your ATS.
We do not do a lot of troubleshooting typically over forums, but I can give you a few thing to get you in the right direction. Please take a look at our k-base document FA156201.
Also, we always recommend that both sources of the ATS be UPSs, since there can be short power blips. Also, what ATS do you have?
See Answer In Context
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login