Important Announcement: Community Back to Full Functionality
Dear Members, we are thrilled to announce that our Community is back to full functionality and that posts publication is now enabled again! We appreciate your patience during the last weeks. Learn more about our Community Guidelines. Thank you, Schneider Electric Community Team.
Maximum number of PM5350 for Daisy chain?
Metering & Power Quality
Schneider Electric support forum about Power Meters (ION, PowerTag, PowerLogic) and Power Quality from design, implementation to troubleshooting and more.
Link copied. Please paste this link to share this article on your social media post.
James is correct from a systems performance point of view. Indeed I would say for 5 second updates I'd go as low as 6 devices, depending somewhat on device type. Most of this is due to device communications latency and the PME comm architecture (multiple clients asking for different data from the same device) and not the RS-485 spec. If the system does not require reasonably fast real time response then more devices can be on one line.
From a hardware specification point of view the RS-485 spec allows for 32 devices per loop and a wiring length of 4000' / 1000 m.
As one gets gets more devices and longer wiring lengths strict adherence to the spec is required, i.e. no stubs or T's or taps are permitted, the cabling must be designed to RS-485 (correct impedance) etc.