EcoStruxure IT forum
Schneider Electric support forum about installation and configuration for DCIM including EcoStruxure IT Expert, IT Advisor, Data Center Expert, and NetBotz
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
This question was originally posted on DCIM Support by Andrew Smith on 2019-11-08
We have a sensor returning a utilisation percentage and would like to convert it to KW by multiplying the max KW of the cooling unit. Can we do this conversion in the DDF, and if so, how do we do it?
This answer was originally posted on DCIM Support by spezialist on 2019-11-08
Dear Andrew Smith,
Of course, this is possible. It will be correct to do this on a special DDF resource, finding your device and making a request to modification.
Hope this helps you.
. Last Modified:
This question is closed for comments. You're welcome to start a new topic if you have further comments on this issue.
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login