Important Announcement: Community Back to Full Functionality
Dear Members, we are thrilled to announce that our Community is back to full functionality and that posts publication is now enabled again! We appreciate your patience during the last weeks. Learn more about our Community Guidelines. Thank you, Schneider Electric Community Team.
APC UPS Data Center & Enterprise Solutions Forum
Schneider, APC support forum to share knowledge about installation and configuration for Data Center and Business Power UPSs, Accessories, Software, Services.
Link copied. Please paste this link to share this article on your social media post.
Posted: 2021-06-2605:39 AM
This was originally posted on APC forums on 7/21/2012
The UPS we just replaced with new batteries is now in normal operation but sometimes shows bypass which I believe is a false alarm. Also noticed charging voltage for 192 cells per bank is only 384VDC, please advise.
BTW, anybody knows the default password for SL40KH?