Link copied. Please paste this link to share this article on your social media post.
Posted: 2021-07-0105:53 AM
Percent of Load for Symmetra LX (N+1 vs N+0)
This was originally posted on APC forums on 7/16/2014
I have two identical LX units installed in one of our server rooms. They are both running the same versions of the UPS firmware, and the same version of the monitoring card (AP9631) firmware (6.1.1)
I just noticed that one is reporting % of load (in watts) at N+0 AND at N+1. The other one is only reporting % of load at N+0. I had been thinking about posting a recommendation that APC include the N+1 figure in a future firmware release. But it seems like you already do (sometimes). I also have several RM 6000 units, and would love to see what the % of load is at N+1 on those units as well.