APC UPS Data Center & Enterprise Solutions Forum
Schneider, APC support forum to share knowledge about installation and configuration for Data Center and Business Power UPSs, Accessories, Software, Services.
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
This question was originally posted by Troy on APC forums on 9/26/2016
I need to reset the SYBT5 battery module so the data is read correctly by the Symmetra LX.I can't find the option to do this.
This reply was originally posted by Haseeb on APC forums on 9/26/2016
Please can you clarify what you mean by reset SYBT5 battery module. Is it a specific battery unit that is causing problems?
Can you please provide your UPS configuration, i.e..
1) How many battery modules do you have in the UPS?
2) Please provide the battery serial numbers.
2) How many power modules do you have in the UPS?
3) What is the UPS loading percentage?
See Answer In Context
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login