Schneider Electric support forum about SmartConnector applications for integration of other building management systems (BMS) into EcoStruxure Building Operation.
Invite a Colleague
Found this content useful? Share it with a Colleague!
. Last Modified:
Link copied. Please paste this link to share this article on your social media post.
When our EWS server changes the value of an ItemValues it takes ~30 seconds until the new value is updated in the EBO's Watch pane.
When I check the value in the EWS Server in SmartConnector's portal, the value is updated immediately.
Any idea why?
By default, EBO only polls for updated values from an EWS server every 60 seconds.
Please take a look at the properties of the EWS Interface in EBO and see what the value in "Value Poll Internal (s)" is. Feel free to reduce this down to something lower.
See Answer In Context
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login