EcoStruxure IT forum
Schneider Electric support forum about installation and configuration for DCIM including EcoStruxure IT Expert, IT Advisor, Data Center Expert, and NetBotz
Invite a Colleague
Found this content useful? Share it with a Colleague!
Link copied. Please paste this link to share this article on your social media post.
We have a problem with wrong temp unit in Active Alarms. All temp values are in C but on Active Alarms we can find F values.
Client and operation system is set on MetricWhere can be a problem?
Events & webinars
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Register today for FREE
Already have an account? Login