Analog Producer value located in an RP-C controller cannot command light object(BACnet type: crs-lighting-output) or blind object(BACnet type: crs-blind-output) located in another RP-C's CRS expansion module.
EcoStruxure Building Operation
- Building Operation Room Controller (RPC) 24 V
- Building Operation Room Controller (RPC) 230 V
Light and Blind objects support only two priorities (1 - Force, 2 - Normal). An error will be returned by the RP if the Priority in the Write request from the Producer Value is outside this range, ex. Priority 16.
In the Analog Producer Value, set the default priority for writing to 2 (normal) or 1 (Force), as shown in below screenshot: