It's your place to connect with experts and peers, get continuous support, and share knowledge.
Contact SchneiderCommunity.Support@se.com if you have any questions.
I've attached a delete device script that will work on a PME 9.0 system. Some new tables were added to ION_Data, so the queries needed to be updated.Please do not give out this script externally!
Power Monitoring Expert 8.2This post is in regards to a bug with the Micrologic driver that results in a steady stream of system log events like this:Should this happen, no event records will uploaded from the devices referenced in the errors.Good ne…View more
The Device Type Editor (DTE) will finally be formally released as part of PME 9.0. The old, familiar MDI is being removed because it is an old VB6 component, and VB6 is no longer supported on newer operating systems.I realize that the MDI is a heavil…View more
As of Power Monitoring Expert 8.2, Database Manager will not upgrade ION Enterprise 6.0.1 and older databases. This has implications for archived databases. If the Configuration Manager tool is used to upgrade ION Enterprise 6.0.1 systems, it will al…View more
For example, if a CM4000 is replaced by a PM8000, some data from the PM8000 may not get uploaded. This problem is not confined to the CM4000 to PM8000 swap out, but will likely happen if a Power Logic meter is replaced by an ION meter.To be clear, th…View more
Problem Description:Data from CM2000 onboard logs can sometimes show large data spikes, particularly for the energy readings. This problem can occur in all versions of PME.Attached are hot fixes for PME 7.2.2 and PME 8.0. It is important to match hot…View more
This hot fix addresses the following Vista issues:1. When an event was acknowledged in the Vista Global Event Viewer, the cursor would change to an hourglass and stay like that until Vista is restarted.2. The Vista scrolling graph display object woul…View more
This hot fix addresses the following VIP issues. It is for PME 8.1 only.1. The VIP Data Monitor module events were processd incorrectly. Both ON and OFF transitions generate independent alarms visible in the Active Alarms page in the Alarms web appli…View more
|Date Last Visited||
2022-03-09 12:29 PM