Hazard of Electric Shock: Remove all power from all devices before removing any covers or doors of the system. Disconnect power at the device and at the power source.
Electrostatic Discharge Required: Always discharge static electricity from your person by touching metal prior to handling any hardware. Failure to do so may result in damage to devices.
Page 1031 of the hardware reference guide only states wire cross-sectional area: 0.34 to 2.5 mm2 (22 to 14 AWG) and not the number of wires allowed to terminate.
EcoStruxure Building Operation
- Building Operation Room Controller (RPC) 24V
- Building Operation Room Controller (RPC) 230V
It is OK to terminate up to 2 wires into each terminal as long as the total area of the wires does not exceed 2.5mm2.