It's your place to connect with experts and peers, get continuous support, and share knowledge.
Contact SchneiderCommunity.Support@se.com if you have any questions.
This was originally posted on APC forums on 3/3/2014HiWe are wanting to read SNMP data for the following UPSes:SUA5000RMI5USUA3000RMI2USMT750I (actually they're Fujitsu branded FJT750I)All UPSes have an AP9630 management card.Where can I find MIB fil…View more
This was originally posted on APC forums on 7/1/2014HiDoes anyone know the default shutdown delay on a BR900GI , the time delay after a shutdown command is received and the actual shutdown.I heard the default is 90 seconds but would like to check.I c…View more
This was originally posted on APC forums on 10/1/2013HiI have a APC Back-UPS ES 400 (model BE400-UK).I would like to know if the battery can be replaced while the unit is still powering the connected devices.Any help appreciated.Thanks!
This was originally posted on APC forums on 3/3/2014Hi,We have ordered a SUA5000RMI5U - it was supplied with a few C13 IEC power cords for connecting equipment to the UPS, but the larger power cord that actually supplies the UPS itself with power was…View more
This was originally posted on APC forums on 10/10/2013HiI have a Back-Ups ES 400 (BE400-UK) which is just over a week old. The Quality assurance thing that came with it has a date of 13-May-2013 so I assume the unit is almost brand new.On the runtime…View more
This was originally posted on APC forums on 5/28/2015Hi I have a BR900G which was purchased in June 2014. apcaccess reports the manufacturing date of the battery as August 2013. For the purposes of replacing the battery after 3 years, should we go fr…View more
This was originally posted on APC forums on 1/20/2015Hi I have a BR900GI connected to my server with the USB cable running apcupsd. I notice if I hold down the power button for 6 seconds and force a self-test, I get this output when I run apcaccess: …View more
|Date Last Visited||
2021-06-24 11:28 PM