It's your place to connect with experts and peers, get continuous support, and share knowledge.
Contact SchneiderCommunity.Support@se.com if you have any questions.
You can subscribe to this forum after you log in or create your free account..
Posted: 2018-05-30 12:40 PM . Last Modified: 2021-11-07 10:55 PM
Check out the EcoStruxure Building Global Demo and tell us what you think! Your feedback will help prioritize and guide enhancements to the EcoStruxure Building demo with future software releases and new functionality.
About the Demo:
We are proud to offer a new demo that features high-end graphics and multiple EcoStruxure Building offers. This demo showcases the power to build a deeply integrated solution across all building systems. It focuses on Edge Control software (EcoStruxure Building Operation), as well as select apps and services, to illustrate the integration functionality and capabilities that EcoStruxure Building delivers for end users, as well as some functionsl for facility managers.
Online access is available via the EcoStruxure Building Operation WebStation client and direct link on the Exchange Extranet.
Local access is available by downloading the demo from the Exchange Extranet, for offline use on local laptops and in demo centers.
Feedback Wanted! Please share your feedback and suggestions on any of the following topics:
Learn more and find all links in MA-00671 (updated!) on The Exchange Extranet.
Posted: 2018-05-30 12:45 PM
Originally submitted by user mitch zawacki.
Here are my comments and suggestions on the 2.0 demo
|#1||Schneider electric building/HVAC/Office Level 00||System navigation||Shows the location of where you are in the navigation list on the top bar||The user(s) should have the ability to move around the levels or areas by left clicking through the navigation bar. The demo currently does not allow for this|
|#2||Schneider electric building/HVAC/Office Level 00, 01,02||Graphics||Floor plan graphic links||Clicking on any of the floors brings up the same graphic and does not change the Office level designation. The levels should slightly differ or at least change the floor designation|
|#3||Schneider electric building/HVAC/Office Level 00, 01,02||Graphics||Can only hover over the space and adjust setpoints||Add Equipment graphics serving the stationary, HR, CEO, main office, small office, store room, breakroom. Add a VAV with hot water reheat, with a space adjustable sensor with an occupancy sensor, and add fin tube radiation for exterior walls. Allow the user to only see the equipment similar to what they would see on their own system. Allow for setpoint/occupancy adjustment through the graphics and link the heating/cooling/air sources on the graphics|
|#4||Schneider electric building/FCU Overview||Graphics||Shows return air temperature sensor||Add the space temperature and setpoint and occupancy sensor|
|#5||Schneider electric building/FCU Schematic||Graphics||Shows return air temperature sensor||Add the space temperature and setpoint and occupancy sensor|
|#6||Schneider electric building/FCU Overview/Schematic||Product data||Add a hyperlink/ to the documents folder to the as-built or sequence of operations|
|#7||Schneider electric building/FCU Overview/Schematic||Product data||Add a controller diagram showing the point names and the current state of the data (i.e. Output #1 FCU Enabled)|
|#8||Schneider electric building/HVAC/Office Level 00, 01,02||Graphics||Displays only Celsius||Show temperatures in Fahrenheit or has have a drop down selection|
|#9||Schneider electric building/HVAC/Office Level 00, 01,02||Graphics||No OSA RH/CO2||Add Outside air RH, and CO2 data|
|#10||Schneider electric building X||Shown a diagram of all of the Enterprise Architechture with multiple automnation servers for EcoSBO. It helps to give a visual when discussing network architecture|
|#11||Schneider electric building/HVAC/Level X||Graphics||Add a ductwork overlay button showing equipment location and duct work runs with thermostat locations shown. Hyperlink the equipment to a graphic, display unoccupied (dimmed out) or occupied (non-dimmed) equipment either when in heating (red) or cooling (blue) modes. This is a demo to shown off all of the bells and whistles, not necessarily at standard for graphics|
|#12||Schneider electric building/AHU-Overview||Graphics||Limited number of data points shown compared to the schmatic||add the data points shown on the schematic to the overview|
|#13||Schneider electric building/AHU-Overview||Graphics||No moving animation for the: supply fan or return fan, dampers, valve, piping etc…)||Add in animations or "cut aways" of the equipment displaying the fans are moving, add position of the valve or valve command and display the hot/chilled water water flows with either blue or red feeding the coils or similar to the PHE-overview|
|#14||Schneider electric building/AHU-Overview||Graphics||Filter - clean||Allow the demo to select dirty filter and show a cut away of the unit with a filthy filter gunked up.|
|#15||Schneider electric building/AHU-Overview||Demo function||Notes - left click on notes and it won't allow for editting||Allow the notes area to be editted|
|#16||Schneider electric building/AHU-Schematic||Graphics||Shows coils||Label each of the coils (pre-heat/chilled water coil/hot water coil)|
|#17||Schneider electric building/AHU-Schematic||Graphics||No mixed air/return air damper||I would suggest adding a return air damper and mixed air temperature sensor. Most new buildings have a return/mixed air damper to recover or reuse the building return air if the outside air is not favorable|
|#18||Schneider electric building/AHU-Schematic and overview||Graphics||Heating/cooling sources - not hyperlinked to the source||Hyperlink the AHU heating/cooling coils to the heating or cooling source (graphic for the PHE or Chilled water system)|
|#19||Schneider electric building/LTHW Circuit/Overview||Graphics||No moving animation for the: pumps and water flow||Add a cut away view of the pumps moving, animate the water moving on the right side of the drawing|
|#20||Schneider electric building/LTHW Circuit/Overview||Graphics||Shown which pipes are supply or return|
|#21||Schneider electric building/LTHW Circuit/Overview||Graphics||Limited number of data points shown compared to the schmatic||add the data points shown on the schematic to the overview|
|#22||Schneider electric building/LTHW Circuit/Schematic||Graphics||Flue Fan||add an animation for the fan being ON|
|#23||Schneider electric building/LTHW Circuit/Schematic||Graphics||Pump labels (duplicated)||Just relabel the pumps (CT-P1,P2 and VT-P1,2)|
|#24||Schneider electric building/Chiller overview/Overview||Graphics||Limited number of data points shown compared to the schmatic||add the data points shown on the schematic to the overview|
|#25||Schneider electric building/PHE Circuit/Overview||Graphics||Limited number of data points shown compared to the schmatic||add the data points shown on the schematic to the overview|
|#26||Schneider electric building||Graphics||Valve position||Throughtout the demo there are valve positions indicated but they do not show if they are 43% OPEN or 43% CLOSED. Just add a label into the demo. Some facilities or new customers may not understand the differences|
|#27||Schneider electric building - Building Meters |
(for the HVAC BMS)
|Graphics||Nothing||Add in the following meters site: power, gas, electric, water, PV solar and display the current reading, week to date, year to date and trend the data|
|#28||Schneider electric building/Plant Room/power/Data hall CRAH 01||Entire unit||Not listed on HVAC||Add this unit to the HVAC Menu|
|#29||Schneider electric building/Plant Room/power/Data hall CRAH 01||Graphics||Limited number of data points shown compared to the schmatic||add the data points shown on the schematic to the overview|
|#30||Schneider electric building/Plant Room/power/Data hall CRAH 01||Docs/notes||Missing all assoicated documents/notes are not enabled|
|#31||Schneider electric building/lighitng/office level 0,1,2,3||Graphics||Lighting zones||Show the hallways and stairwell as lighting zones|
|#32||Schneider electric building/lighitng/office level 0,1,2,3||Graphics||have a selection button to enable a graphic overaly of the lighting fixtures and show a difference between standard lights and the emergency lights|
|#33||Schneider electric building/lighitng/office level 0,1,2,3||Graphics||Office lighting legend||Maybe change the 0,25,50,75,100 percentage colors to difference colors rather than difference shades|
|#34||Schneider electric building/lighitng/office level 0,1,2,3||Graphics||Add a lighting panel or zone overview and display daylight harvesting in the applicable zones|
|#35||Schneider electric building/lighitng/office level 0,1,2,3||Graphics||Show the light switch locations and allow EcoSBO to switch them ON/OFF/Dimming capabilities etc…|
|#36||Schneider electric building/fire/office level 0,1,2,3||Graphics||On the top left display IN ALARM and list the zones IN ALARM|
|#37||Schneider electric building/fire/office level 0,1,2,3||Graphics||Firemans panel||get a higher resolution panel and allow for interaction between EcoSBO and the panel|
Posted: 2018-05-30 12:47 PM
Originally submitted by user Adam Wright
Thank you for your feedback your comments will be very useful for the version 2.0 demo which we are working on at the moment.
Posted: 2018-05-30 12:48 PM
Originally submitted by user Matthew Allard
Thanks for the thorough and documented comments on the demo! Greatly appreciated!
Posted: 2019-08-18 09:54 PM
I restore this demo in EBO v18.104.22.168, but I only view by account Demo and i don't know account administrator, and i can't restore my old backup in EBO again.
Can you help me this proplem ?
Posted: 2019-08-19 12:36 AM
The username and password would usually be admin/admin. You can contact technical support to get the password reset, or you can DFU the device and install a new blank database.
Posted: 2019-08-19 12:47 AM
i used username and password admin/admin but error, I restore https://ecobuilding.schneider-electric.com/search?documentUUID=d192fb1c-f62f-4931-bff5-e8c363b6838b&... this demo .
Posted: 2019-08-19 12:51 AM
The above doesn't seem like an error but an information dialog.
Did you review the TPA linked in the initial description here?
Use the following credentials to enter the demo:
User Name: buildingcontrol
Posted: 2019-08-19 12:59 AM
Yes, I only use account demo, but i need restore my backup in EBO , this demo Backup only use to view, but i need restore EBO with my backup.
This demo i think it is demo offline, i can login by administrator, but don't my thinking.
Posted: 2019-08-19 06:28 AM
If you want to load a database that you have created, you can:
1. DFU the device (press reset 3 times quickly).
2. Use device administrator to "upgrade database" and choose "new database"
3. log in with admin/admin
4. restore your database.